Air Mixing Box Model MB
Provide as shown KEES Air Mixing Box Model MB with Air Mixer of .081" aluminum, or 304 or 316 stainless steel construction of size, performance and maximum pressure drop indicated. The plenum shall be fabricated of 18 gauge galvanized steel with 1", 1-1/2# density fiberglass duct liner (or 22 gauge solid (or perforated) liner over 1", 1-1/2# density duct liner) (or uninsulated). The plenum shall have inlet collars with Ductmate flanges, drilled flanges on outlet for mating to adjacent section, low leakage parallel blade dampers with leakage of less than 10 C.F.M. per sq. ft. at 3" W.G., mounting legs or rails as required and other options as listed. The Air Mixer shall mix two or more air streams of differing temperature to within +/- 6 degrees Fahrenheit of theoretical mixed air temperature and provide a more uniform air velocity contour entering a downstream filter or coil bank. For more details, refer to KEES catalog AMB.
Back to: Air Mixers